10/31/2018 - 16:12
We were contacted by one of our customers as their current cold-water booster set had a failed motor and inverter. The problem was the controls on the set were obsolete and the replacements will not communicate with the other controllers.
04/18/2018 - 12:04
We were contacted by the facilities department at the Tower of London as the existing heating pressurisation unit had failed. We carried out a full onsite survey and concluded that the unit was not worth repairing and due to
12/18/2017 - 10:20
Pumps UK were contacted by a company that specialise in energy saving recently, and we were asked to carry out a life cycle survey on all the heating pumps for a building at Royal Arsenal.
07/19/2017 - 16:30
We were recently asked to replace a chilled water pressurisation unit in an office block in central London. The old pressurisation unit that was installed had failed and the parts were obsolete.
05/30/2017 - 16:21
Recent upgrade in Kingston of an old belt driven pump for a new direct driven Lowara NSCS. We used crimped fittings on the new pipework to speed the install and get the system running.